0007 00 14
Table 9. Generator Container Fire Suppression System Operator Controls and Indicators.
CONTROL OR INDICATOR
Control Module BATTERY
The control module battery LED indicator is lit when the fire
suppression system is operating on battery power.
Control Module POWER
The control module power LED indicator is lit when power is
supplied to the fire suppression system.
Control Module ALARM
Alarm LED indicates that an alarm has been initiated. Upon
receiving an alarm input signal, the LED flashes once per second.
After the alarm shutdown time delay has expired, the LED flashes
three times per second. After fire suppression system discharge,
the LED flashes once every six seconds to indicate that fire
suppression has occurred.
Control Module DETECTION
The detection LED lights when the fire detection devices send a
signal to the control module that a fire has been detected.
Control Module RELEASE
The release LED lights when the fire suppression system releases
the fire extinguishing agent.
The reset button allows the operator to perform the following
functions: set relays in correct position upon installation, reset
and/or defer alarm-to-shutdown delay if pressed or held down
during the period, reset control module after system operation
when replacement of detection wire/thermal detectors is complete.
The delay button allows the operator to repeat the shutdown time
delay, if pressed before the shutdown time delay has expired.
Pull ring pin to allow manual activation of fire
Manual Actuator Knob
Manually activates fire suppression system for immediate
discharge of fire extinguishing agent.
Electric Manual Pull Station
Manually initiates fire suppression system. Lift lever to actuate.
Time delay circuit will activate.
15 KW Tactical Generator Pneumatic
Cutoff switch is pneumatically activated when the fire suppression
system is discharged. Cutoff switch must be reset before
attempting to start the 15 KW tactical generator.