0028 00 1
GENERATOR CONTAINER FIRE SUPPRESSION SYSTEM
OPERATION UNDER USUAL CONDITIONS
OPERATING PROCEDURES - OPERATE GENERATOR CONTAINER FIRE
TEST CONTROL MODULE LED INDICATORS AND SOUNDER
Fire in protected compartments or accidental activation of the CO2 system while
personnel occupy compartment could result in loss of life if CO2 is released.
Personnel must listen for siren, recognize its sound and evacuate space
immediately (within 30 seconds).
Do not depress fire suppression control head lever during normal maintenance.
Death or injury to personnel could occur if CO2 is inhaled.
Prior to entering the shelter after discharge of CO2, the shelter shall be completely
cleared of any CO2 that may remain. Death or injury to personnel could occur if
CO2 is inhaled.
Locate control module.
Press RESET button (1) to illuminate LED indicators and activate sounder.
Refer to troubleshooting procedures if light or sounder is inoperative.