0007 00 12
Control Module POWER LED Indicator
The control module power LED indicator is lit when
power is supplied to the fire suppression system.
Control Module ALARM LED Indicator
Alarm LED indicates that an alarm has been
initiated. Upon receiving an alarm input signal, the
LED flashes once per second. After the alarm
shutdown time delay has expired, the LED flashes
three times per second. After fire suppression
system discharge, the LED flashes once every six
seconds to indicate that fire suppression
Control Module DETECTION LED Indicator
The detection LED lights when the fire detection
devices send a signal to the control module that a
fire has been detected.
Control Module RELEASE LED Indicator
The release LED lights when the fire suppression
system releases the fire extinguishing agent.
The reset button allows the operator to perform the
following functions: set relays in correct position
upon installation, reset and/or defer alarm-to-
shutdown delay if pressed or held down during the
period, reset control module after system operation
when replacement of detection wire/thermal
detectors is complete.
The delay button allows the operator to repeat the
shutdown time delay, if pressed before the shutdown
time delay has expired.
Pull ring pin to allow manual activation of fire
Manual Actuator Knob
Manually activates fire suppression system for
immediate discharge of fire extinguishing agent.
Electric Manual Pull Station
Manually initiates fire suppression system. Lift lever
to actuate. Time delay circuit will activate.
15 KW Tactical Generator Pneumatic
Cutoff switch is pneumatically activated when the
fire suppression system is discharged. Cutoff switch
must be reset before attempting to start the
Table 10. Generator Container Fire Suppression System Operator Controls and Indicators.