0014 00 1/2 blank
UNIT, DIRECT SUPPORT AND GENERAL SUPPORT MAINTENANCE
ROLL-ON/ROLL-OFF DISCHARGE FACILITY
HIGH/LOW GENERATOR OUTPUT VOLTAGE
Generator output voltage is too high or low (normal is 120 VAC).
Engine is oscillating during operation.
Adjust engine speed as required. Contact depot maintenance.
Engine power is low.
Adjust engine power as required. Contact depot maintenance.
Electrical output is unstable.
Make electrical load adjustments as required. Contact depot maintenance.
Loose wire connections.
Check for loose connections and tighten as necessary.
Perform operational check of light tower engine. (TM 55-1945-205-10-2)
END OF WORK PACKAGE